The North Carolina Building Code Council has adopted the 2011 NEC as the North Carolina Electrical Code.
The official effective date
of the 2011 North Carolina Electrical Code (NEC) is July 3, 2012.
Article 10 - ADMINISTRATIVE SECTION
These Administrative Regulations along with the requirements included in the 2011 Edition of the National Electrical Code (NFiPA-70 - 2011) as approved by the North Carolina Building Code Council on June 14, 2011, to be effective September 1, 2011, with the following amendments:
(1) 210.8(a)(3) (Exception No. 2)
(3) 334.15 Exposed Work
shall be known as the North Carolina Electrical Code, and may be cited as such or as the State Electrical Code; and will be referred to herein as "the code" or "this code".
Article 80 Administration and Enforcement of the code is hereby not adopted and does not apply for this code. For Scope and Exceptions to Applicability of Technical Codes, refer to the North Carolina Administrative Code and Policies.
The purpose of the code is to provide minimum standards, provisions and requirements of safe and stable design, methods of construction and uses of materials in buildings or structures hereafter erected, constructed, enlarged, altered, repaired, moved, converted to other uses of demolished and to regulate the electrical systems, equipment, maintenance, use and occupancy of all buildings or structures. All regulations contained in this code have a reasonable and substantial connection with the public health, safety, morals, or general welfare, and their provisions shall be construed liberally to those ends.
For administrative regulations pertaining to inspection (rough-ins and finals), permits and Certificates of Electrical Compliance, see local ordinances and the North Carolina Administrative Code and Policies. When the provisions of other codes are determined to be contrary to the requirements of this code, this code shall prevail.
Unless the context indicates otherwise, whenever the word "building" is used in this chapter, it shall be deemed to include the word "structure" and all installations such as plumbing systems, heating systems, cooling systems, electrical systems, elevators and other installations which are parts of, or permanently affixed to, the building or structure.
10.6 APPLICATION OF CODE TO EXISTING BUILDINGS
For requirements of existing structures, refer to the North Carolina Administrative Code and Policies.
10.7 Service Utilities
10.7.1 Connection of Service Utilities
– No person shall make connections from a utility, source of energy, fuel or power to any building or system which is regulated by the technical codes until approved by the Inspection Department and a Certificate of Compliance is issued (General Statute 143-143.2)
10.7.2 Authority to disconnect Service Utilities
– The Inspection Department shall have the authority to require disconnecting a utility service to the building, structure or system regulated by the technical codes, in case of emergency or where necessary to eliminate an imminent hazard to life or property. The Inspection Department shall have the authority to disconnect a utility service when a building has been occupied prior to Certificate of Compliance or entry into the building for purposes of making inspections cannot be readily granted. The Inspection Department shall notify the serving utility, and whenever possible the owner or occupant of the building, structure or service system of the decision to disconnect prior to taking such action. If not notified prior to disconnecting, the owner or occupant shall be notified in writing within eight (8) working hours (General Statutes 143-143.2, 153A-365, 153A-366, 160A-425 and 160A-426). NORTH CAROLINA ELECTRICAL CODE, 2008 EDITION
10.8 Temporary Power
The provisions of this section apply to the utilization of portions of the wiring system within a building to facilitate construction.
10.8.2 Provisions for Temporary Power.
The Code enforcement official shall give permission and issue a permit to energize the electrical service when the provisions of 10.8 and the following requirements have been met:
1) The service wiring and equipment, including the meter socket enclosure, shall be installed, the service wiring terminated, and the service equipment covers installed.
2) The portions of the electrical system that are to be energized shall be complete and physically protected.
3) The grounding electrode system shall be complete.
4) The grounding and the grounded conductors shall be terminated in the service equipment.
5) At least one receptacle outlet with ground fault circuit interrupter protection for personnel shall be installed with the circuit wiring terminated.
6) The applicable requirements of the North Carolina Electrical Code apply.
10.8.3 Uses Prohibited.
In no case shall any portion of the permanent wiring be energized until the portions have been inspected and approved by an electrical Code Enforcement Official. Failure to comply with this section may result in disconnection of power or revocation of permit.
10.8.4 Application for Temporary Power. Application for temporary power shall be made by and in the name of the applicant. The application shall explicitly state the portions of the energized electrical system, mechanical system, or plumbing system for which application is made, its intended use and duration.
10.8.5 Security and Notification.
The applicant shall maintain the energized electrical system or that portion of the building containing the energized electrical system in a secured and locked manner or under constant supervision to exclude unauthorized personnel. The applicant shall alert personnel working in the vicinity of the energized electrical system to its presence.
10.9 Requirements of Other State Agencies, Occupational Licensing Boards, or Commissions
The North Carolina State Building Codes do not include all additional requirements for buildings and structures that may be imposed by other State agencies, occupational licensing boards, and commissions. It shall be the responsibility of a permit holder, design professional, contractor, or occupational license holder to determine whether any additional requirements exist.
• For general permit information, please call 704-336-3830
• For general electrical code questions, please call CTAC 704-432-4668
• For Code Interpretations, please call Joe Weathers, Electrical Code Administrator, 704-336-5379